Are you looking for a professional Power Quality Audit Report? If you've been feeling stuck or lack motivation, download this template now!
Do you have an idea of what you want to draft, but you cannot find the exact words yet to write it down or lack the inspiration how to make it? If you've been feeling stuck, this Power Quality Audit Report template can help you find inspiration and motivation. This Power Quality Audit Report covers the most important topics that you are looking for and will help you to structure and communicate in a professional manner with those involved.
www.wisemgmtsys.com Final Report: Friday, July 29, 2011 Energy Audit Report Rev: 00 Confidential 1 WISE Management Systems Energy Audit Report IND/TPR/EMP/005/011 ELTEX Energy Audit Report of ELTEX Super Castings (Coimbatore) – Final Summary Report Project Report Title: Energy Audit Report Work Order No: WO/MNT/2011/03 dated 26th May 2011 Client Name: Eltex Super Castings Plant Location: ELTEX Super Castings, A Division of KLRF, Periyanaickenpalayam, Coimbatore -641020 Sanctioned Demand: 1925 kVA Maximum Demand Reached: 1885 kVA Power Factor Achieved in Year 2010: 0.94 to 0.97 Date of Report: Friday, July 29, 2011 Name of the Auditing Company: WISE Management Systems, No.. S/L Energy Saving Opportunities Savings Investments Payback 1a Auxiliary Transformer Tap Position Change 2,43,000 NIL Immediately 1b Automatic Voltage Regulator 1000 KVA Same as 1 a 1,20,000 0.5 Years 2a APFC Panel for MV Panel, 12 stages 200 KVAr Capacitor Bank Enhancement- Improving Power Factor and Reducing KVA Demand 96,420 3,00,000 3.2 Years 2b APFC Panel for GSB 2 incoming , 12 stages 200 KVAr Capacitor Bank Enhancement - Improving Power Factor and Reducing KVA Demand 73,500 3,00,000 4.0 Years Energy Audit Report Rev: 00 Confidential 5 WISE Management Systems S/L 2c Energy Audit Report Energy Saving Opportunities APFC Panel for GSB 3 incoming , 12 stages 200 KVAr Capacitor Bank Enhancement- Improving Power Factor and Reducing KVA Demand IND/TPR/EMP/005/011 ELTEX Savings Investments Payback 1,02,900 3,00,000 2.9 Years 3 Lighting Systems (Installation of Servo Stabilizer for GSB 2) 2,04,960 2,00,000 1 Year 4 Lighting Systems- Change to HPMV Maps and Energy efficient Copper Chocks 2,40,667 1,98,000 1 Year 5 Change to energy efficient motors for Compressors (90 KW and 75 KW) 74,250 2,00,000 2.6 Years 6 Various Continual Improvements and optimization to Compressed Air Systems 9,72,000 2,00,000 0.25 Year 7 Total 20,07,697 18,18,000 0.9 Year -Estimated based on rough estimates (Separate Proposal
Feel free to download this intuitive template that is available in several kinds of formats, or try any other of our basic or advanced templates, forms or documents. Don't reinvent the wheel every time you start something new...
Download this Power Quality Audit Report template and save yourself time and efforts! You will see completing your task has never been simpler!